Please forward this error screen to 69. This domain name is for sale. How to fix a water softener: how to diagnose problems with a water softener that is not working, or how to diagnose deposits on plumbing faucets and fixtures where a water softener is installed. Fix a Water Softener that Is How to diagnose and fix everything electronic pdf Working Properly – How to diagnose water softener operation problems.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website. This article series describes procedures for diagnosing and repairing water softener or water conditioner problems including water conditioner control settings and adjustment or repair, brine tank and brine tank float cleaning and repair, and the proper amount of water softening or conditioning that is needed. This water softener repair article describes what to check first if the softener is not working properly. You want first to see that the water softener is not on “bypass” – is household water flowing through the unit? A sketch of an Autotrol bypass valve is shown at left. This valve is an option and may not be installed on your unit.
If the unit uses electricity to run a timer be sure it’s plugged in to a live outlet and has power. Some water conditioners use a low-voltage transformer to power the control – be sure that device is present, plugged in, and working. You can use a simple VOM to check that the transformer is outputting DC at the proper voltage level. Is there salt in the salt tank? Test the water for hardness so that you know how to set the controls. Poke around into the salt to be sure the salt tank is really there.
You may see this as a thin salty film left at faucets or in a dishwasher. Mineral scale may also be a thin hard white deposit but is a separate problem not a too-much-salt problem. Try these water softener diagnosis and repair steps before rushing to replace the water softener itself. Check that the softener is plugged-in, that its electrical circuit is powered-on, that a switch, pull chain, breaker or fuse are all “on” and working.